Wire/cable voltage drop calculator and how to calculate.
* @ 68°F or 20°C
** Results may change with real wires: different material resistivity and number of strands in the wire.
*** For wire length of 2x10ft, wire length should be 10ft.
Optimize your electrical circuit design and power distribution with our Voltage Drop Calculator. Accurately calculate voltage drops, select appropriate wire gauges, and ensure efficient energy transmission. Simplify your electrical projects with this user-friendly tool.
The voltage drop V in volts (V) is equal to the wire current I in amps (A) times 2 times one-way wire length L in feet (ft) times the wire resistance per 1000 feet R in ohms (Ω/kft) divided by 1000:
V_{drop (V)} = I_{wire (A)} × R_{wire(Ω)}
= I_{wire (A)} × (2 × L_{(ft)} × R_{wire(Ω/kft)} / 1000_{(ft/kft)})
The voltage drop V in volts (V) is equal to the wire current I in amps (A) times 2 times one-way wire length L in meters (m) times the wire resistance per 1000 meters R in ohms (Ω/km) divided by 1000:
V_{drop (V)} = I_{wire (A)} × R_{wire(Ω)}
= I_{wire (A)} × (2 × L_{(m)} × R_{wire (Ω/km)} / 1000_{(m/km)})
The line-to-line voltage drop V in volts (V) is equal to the square root of 3 times the wire current I in amps (A) times one-way wire length L in feet (ft) times the wire resistance per 1000 feet R in ohms (Ω/kft) divided by 1000:
V_{drop (V)} = √3 × I_{wire (A)} × R_{wire (Ω)}
= 1.732 × I_{wire (A)} × (L_{(ft)} × R_{wire (Ω/kft)} / 1000_{(ft/kft)})
The line-to-line voltage drop V in volts (V) is equal to the square root of 3 times the wire current I in amps (A) times one-way wire length L in meters (m) times the wire resistance per 1000 meters R in ohms (Ω/km) divided by 1000:
V_{drop (V)} = √3 × I_{wire (A)} × R_{wire (Ω)}
= 1.732 × I_{wire (A)} × (L_{(m)} × R_{wire (Ω/km)} / 1000_{(m/km)})
The n gauge wire diameter d_{n} in inches (in) is equal to 0.005in times 92 raised to the power of 36 minus gauge number n, divided by 39:
d_{n}_{ (in)} = 0.005 in × 92^{(36-n)/39}
The n gauge wire diameter d_{n} in millimeters (mm) is equal to 0.127mm times 92 raised to the power of 36 minus gauge number n, divided by 39:
d_{n}_{ (mm)} = 0.127 mm × 92^{(36-n)/39}
The n gauge wire's cross-sectional area A_{n} in kilo-circular mils (kcal) is equal to 1000 times the square wire diameter d in inches (in):
A_{n}_{ (kcmil)} = 1000×d_{n}^{2} = 0.025 in^{2} × 92^{(36-n)/19.5}
The n gauge wire's cross sectional area A_{n} in square inches (in^{2}) is equal to pi divided by 4 times the square wire diameter d in inches (in):
A_{n}_{ (in}2_{)} = (π/4)×d_{n}^{2} = 0.000019635 in^{2} × 92^{(36-n)/19.5}
The n gauge wire's cross sectional area A_{n} in square millimeters (mm^{2}) is equal to pi divided by 4 times the square wire diameter d in millimeters (mm):
A_{n}_{ (mm}2_{)} = (π/4)×d_{n}^{2} = 0.012668 mm^{2} × 92^{(36-n)/19.5}
The n gauge wire resistance R in ohms per kilofeet (Ω/kft) is equal to 0.3048×1000000000 times the wire's resistivity ρ in ohm-meters (Ω·m) divided by 25.4^{2} times the cross-sectional area A_{n} in square inches (in^{2}):
R_{n (Ω/kft)} = 0.3048 × 10^{9} × ρ_{(Ω·m)} / (25.4^{2} × A_{n}_{ (in}2_{)})
The n gauge wire resistance R in ohms per kilometer (Ω/km) is equal to 1000000000 times the wire's resistivity ρ in ohm-meters (Ω·m) divided by the cross-sectional area A_{n} in square millimeters (mm^{2}):
R_{n (Ω/km)} = 10^{9} × ρ_{(Ω·m)} / A_{n}_{ (mm}2_{)}
AWG # |
Diameter (inch) |
Diameter (mm) |
Area (kcmil) |
Area (mm^{2}) |
---|---|---|---|---|
0000 (4/0) | 0.4600 | 11.6840 | 211.6000 | 107.2193 |
000 (3/0) | 0.4096 | 10.4049 | 167.8064 | 85.0288 |
00 (2/0) | 0.3648 | 9.2658 | 133.0765 | 67.4309 |
0 (1/0) | 0.3249 | 8.2515 | 105.5345 | 53.4751 |
1 | 0.2893 | 7.3481 | 83.6927 | 42.4077 |
2 | 0.2576 | 6.5437 | 66.3713 | 33.6308 |
3 | 0.2294 | 5.8273 | 52.6348 | 26.6705 |
4 | 0.2043 | 5.1894 | 41.7413 | 21.1506 |
5 | 0.1819 | 4.6213 | 33.1024 | 16.7732 |
6 | 0.1620 | 4.1154 | 26.2514 | 13.3018 |
7 | 0.1443 | 3.6649 | 20.8183 | 10.5488 |
8 | 0.1285 | 3.2636 | 16.5097 | 8.3656 |
9 | 0.1144 | 2.9064 | 13.0927 | 6.6342 |
10 | 0.1019 | 2.5882 | 10.3830 | 5.2612 |
11 | 0.0907 | 2.3048 | 8.2341 | 4.1723 |
12 | 0.0808 | 2.0525 | 6.5299 | 3.3088 |
13 | 0.0720 | 1.8278 | 5.1785 | 2.6240 |
14 | 0.0641 | 1.6277 | 4.1067 | 2.0809 |
15 | 0.0571 | 1.4495 | 3.2568 | 1.6502 |
16 | 0.0508 | 1.2908 | 2.5827 | 1.3087 |
17 | 0.0453 | 1.1495 | 2.0482 | 1.0378 |
18 | 0.0403 | 1.0237 | 1.6243 | 0.8230 |
19 | 0.0359 | 0.9116 | 1.2881 | 0.6527 |
20 | 0.0320 | 0.8118 | 1.0215 | 0.5176 |
21 | 0.0285 | 0.7229 | 0.8101 | 0.4105 |
22 | 0.0253 | 0.6438 | 0.6424 | 0.3255 |
23 | 0.0226 | 0.5733 | 0.5095 | 0.2582 |
24 | 0.0201 | 0.5106 | 0.4040 | 0.2047 |
25 | 0.0179 | 0.4547 | 0.3204 | 0.1624 |
26 | 0.0159 | 0.4049 | 0.2541 | 0.1288 |
27 | 0.0142 | 0.3606 | 0.2015 | 0.1021 |
28 | 0.0126 | 0.3211 | 0.1598 | 0.0810 |
29 | 0.0113 | 0.2859 | 0.1267 | 0.0642 |
30 | 0.0100 | 0.2546 | 0.1005 | 0.0509 |
31 | 0.0089 | 0.2268 | 0.0797 | 0.0404 |
32 | 0.0080 | 0.2019 | 0.0632 | 0.0320 |
33 | 0.0071 | 0.1798 | 0.0501 | 0.0254 |
34 | 0.0063 | 0.1601 | 0.0398 | 0.0201 |
35 | 0.0056 | 0.1426 | 0.0315 | 0.0160 |
36 | 0.0050 | 0.1270 | 0.0250 | 0.0127 |
37 | 0.0045 | 0.1131 | 0.0198 | 0.0100 |
38 | 0.0040 | 0.1007 | 0.0157 | 0.0080 |
39 | 0.0035 | 0.0897 | 0.0125 | 0.0063 |
40 | 0.0031 | 0.0799 | 0.0099 | 0.0050 |